Check the level sensor: closed contacts. Voltage 0 Volts or 5 Volts on the control unit leads to a stop by code 102. Correctly set the power of the pump or its characteristic and reconcile with maximum power. Error 502 - The flame is detected when the gas valve is closed. For Buderus boilers with a splitter in the heat exchanger, check whether the splitter is installed.
If the gas still exists, and the unit ignites, and then dries with an error of 501, then check the ionization electrode flame sensor. Check the fan and its cable with a plug, replace if necessary. The burner starts and switches to fault. Error codes and Troubleshooting Troubleshooting is similar to troubleshooting other brands and models. Being a fair way from a major city getting it repaired is going to be a very costly matter and typically it's out of warranty. Any advice would be appreciated.
Error 608 - The pressure switch did not work, but the fan turned on check the pressure switch and all its connections. Check the flue gas system and clean or repair if necessary. Error 5P1 - First ignition attempt failed. Water load solenoid valve malfunction alarm. If the temperature control relay is not connected, then install a jumper 8Y - Temperature monitoring relay blocked Unlock the temperature control relay.
This will release the adhesive easily, without damaging the surface of the washer. Check the connection between the motor and the electronic module. The ambient temperature could be below freezing. Re- programme the machine and restart the wash cycle. If necessary, conduct water treatment and install a dirt trap. Water can slowly seep out of the washing machine down the drain hose and into the drain.
The boiler will turn on automatically if a request for heat is received. The condensate pump does not work - Replace the condensate pump. The electronic controller and the indicating module are successively replaced. Take a note of which lights are flashing, turn the appliance off and call for technical assistance. This article is for those who have a problem with the heater, received an error code and have the tools, knowledge, and experience to deal with the problem.
If the fault persists for a long time, the display shows fault code 4U and operating code 222 4Y - The flow temperature sensor break is defective. Reconnect supply and wait 30 seconds and try starting the machine again. Advice: If the fault remains, we recommend you call our customer service centre to book an engineer on: 0344 822 4224. Check the reliability of locking the door of the hatch. The machine continuously fills with water and continually drains away or Water left in the drum or Stuck on wash. F12: Lack of Display card-Main Card Communication 1.
I've checked the outlet pipe and it's clean. You have checked everything, but the dishwasher still doesn't work and the problem persists? Common faults of the Ariston boilers with codes 607, 6P1, 6P2. Replace the temperature sensor or module. If none of the above solutions work, it is likely you have a pump failure and will need further assistance. So it is not that often that they experience major problems.
Re-programme the machine and restart the wash cycle. This is the reason why this troubleshooting guide exists - to help you solve the problem with water heating and save some money. Therefore, the correct installation of the chimney with a slight downward slope is recommended to drain the condensate. Error 111 - Similar to code 108 for Ariston models with automatic replenishment mode. Also, the model gives a chance to vary the water temperature for the wash and rinse cycles depending on the degree of soil. Error code 551 Solenoid gas valve failure - check the gas pressure and connections. If you try to ignite it with an already damaged handset, it simply does not light up and gives out the error code 6P1.
Allow us to provide you with a perfectly engineered concept that empowers people and businesses to succeed Connecting other people, customers, professionals and companies in search of: A Valuable Articles and Directory information resource. Locate the switch on the computer board and check that it is in the correct position. This is the control panel front or top Indesit. The Buderus boiler burner starts and switches to a fault. When working with the intake of air for combustion from the room, check the air supply to the room and the ventilation openings.
But as a result of overheating, the lower part of the Venturi tube melts slightly. Check it, and if it is defective, replace 3F - The burner and fan have been operating for 24 hours without interruption and are switched off for a short time for safety reasons. If an issue occurs for instance, you washer is not spinning , try the solutions suggested in the tables below. Error code 661 Faulty water bypass - the same procedure as for the flow adjustment valve. The electronics aren't talking to each other properly. Damaged safety temperature limiter - Check and, if required, replace defective parts. Error 102 - Heating circuit pressure sensor defective short circuit or open circuit - Check the sensor voltage on the terminal board and install a new one if necessary.